FURN L/PRESS

Furnace pressure refers to the two flow-switches that monitor water flow in the output inductor bar. If water flow is not present, or dips below the minimum flow value, this fault will trip the unit. Typically this indicates a closed or semi-closed valve, a water leak, or that the heat exchanger pump is not on, or rotating the wrong direction.

VIPs